The web Browser you are currently using is unsupported, and some features of this site may not work as intended. Please update to a modern browser such as Chrome, Firefox or Edge to experience all features Michigan.gov has to offer.
Liquefied Petroleum Gases (LPG)
Storage and Handling of Liquefied Petroleum Gases (LPG) Rules were revised and filed with the Secretary of State on July 7, 2008. The provisions of the National Fire Protection Association Pamphlet No. 58, 2004, entitled "NFPA 58 Liquefied Petroleum Gas Code 2014 Edition," are incorporated by reference and adopted as part of these rules. The regulations cover containers where individual capacity is over 2,000 gallons, aggregate capacity over 4,000 gallons, or any size container filling location. For a copy of NFPA 58, 2004 contact the National Fire Protection Association, Batterymarch Park, Quincy, MA 02269, phone 800-344-3555 (ask for the library).
Liquefied petroleum tanks used in connection with building heating systems and equipment have a dual administration by the Michigan Department of Licensing and Regulatory Affairs, Bureau of Fire Services. A Memorandum of Understanding clarifies the responsibility and requirements of each agency.
Informational Memorandum No. 14: Storage of Liquefied Petroleum Gases.